If I turn my fan on on my thermostats the heat pump turns on with heat or cool setting
There is a jumper wired from green to w1(the heat pump)
If I move the jumper to r (24v) and g and turn on the dip swith 8 (on – fan comes on with call for heat off – fan comes on with cool call) will it fix my problem?
I’m assuming I would have to adjust the dip switch for summer or winter?
We recently got a wood stove in step down den and it has a blower so we want to run the fan to circulate the heat from it
The jumper between W1/Y1 and G on your board is what is causing the fan problem here. So, I would remove the jumper to the G wire (from W1/Y1) from the zone board with the indoor unit OFF at the service switch, flip dip switch 8 on the zone board to ON to make it so that the zone board calls for fan when a heat call comes in, turn the service switch on the indoor unit back ON, and enjoy your newfound comfort!
Answered by ThreePhaseEel on November 29, 2020
Get help from others!